PSC vs. ECM Motors: Know Their Differences
The heating, ventilation and air conditioning (HVAC) industry uses a variety of motor technologies in its equipment. Historically, the two predominant motor types have been permanent split capacitor (PSC) single speed motors and electronically commutated motors (ECM) with variable-speed capability. HVAC professionals understand the key differences between these motor types. This article aims to share those differences to you today.
For many years, PSC single-speed motor technology has been the standard in the HVAC industry. It represents the highest installed base.
PSC motors are considered single-speed (speed refers to rate of rotational motion) because they have no internal controls that can be programmed automatically to vary the rotation of the motor over an operating range. In order to make PSC motors more flexible for various applications, speed taps are included to allow the mechanical contractor to manipulate the motor’s speed to ensure that the correct amount of airflow is delivered. There is, of course, a limit to the amount of static pressure the motor can handle, so it is important to keep in mind the optimal performance and safety. As static pressure increases, a PSC motor’s performance tends to drop off because it cannot adjust torque or speed.
Because of its design, there are some disadvantages intrinsic in PSC motors. They are less efficient than other motors because they consume more watts. They are not ideal for continuous fan operation because since they run close to full speed, they use more energy than what the function requires. This also makes them less attractive for other continuous filtration applications. They are also the least quiet among the motor technologies. They do not offer customized airflow patterns that are often critical when it comes to managing humidity.
ECM variable speed motor technology is highly variable and is ideal for various advanced applications.
ECM technology is based on a direct current (DC) design that is more efficient and it runs cooler than AC PSC motors. They are, in fact, approximately 80% efficient compared to the 60% efficiency rating of PSC designs. ECM motors are programmable. In the case of a failure, the control or the motor can be replaced without having to replace the entire unit. They are also designed to run over a wide range of speeds, making them ideal for delivering airflow in a multitude of system designs. They also draw the least amount of watts, making them the most efficient motor technology. They are also the quietest among the motor technologies since they have the ability to ramp up and down slowly, making them ideal for certain applications with noise concerns.
When it comes to disadvantages, ECM variable-speed motors come at a premium cost.
To see the difference in performance between the two types of motors, check out this chart:
*Chart data courtesy of: Biemayer, P., Lutz, J., & Lekov, A. (2004). Measurement of airflow in residential furnaces*